Decreasing Water Pressure
My wife and I have noticed that the water pressure in our house is sometimes very poor. Is this something we should be concerned about? Or is it just due to too many people in our neighborhood taking showers/using water at the same time?
RI in Pasadena, CA
It is unlikely that your neighbors' water use would affect your water flow. The size of the pipes used for municipal water supplies is large enough to keep the flow even to all homes, even if everyone turned their taps on at once. I would contact the company that manages your public water supply to see what experience they have with this problem.
Generally speaking, a draw on your water system in one part of your home will affect the pressure elsewhere, depending of course on the size of your home's pipes, the starting pressure and the volume of water flow. A garden hose, for example, will have a more dramatic effect than a toilet, since the volume of moving water is greater. Also, there are "automatic" systems that might cause temporary draws you might not be aware of at the time the pressure drops, such as self-cleaning water softening systems, sprinkler systems or automatic refilling of a heating system.
If you happen to be on a well system, variations of water pressure are normal. Some folks who are accustomed to the constant pressure of "city water" are astounded at the difference! Showers have to be carefully planned around toilet flushes, dishwashing and, of course, the laundry. Or else there may be lots of screaming!
Residential well systems operate within a range of pressures. Keeping the pressure absolutely constant would require the pump to cycle on every time you drew water, increasing the wear on the pump dramatically. This would also cause you to experience a "pulsing" in the water as each cycle of the pump moves water.
You should also investigate whether your home has an automatic pressure adjusting system. Some municipal water supplies have such high pressure that residents install pressure-reducing equipment. A malfunction with this system could possibly cause unwanted pressure variations.
Of course, there could be other hidden factors I have missed. In which case you might want to have a plumber inspect your system for other pressure "bottlenecks".
Have a small home repair question for THE NATURAL HANDYMAN? Just click here www.naturalhandyman.com/aitikia
For more home repair information, visit NH's growing list of original home repair articles and quality links www.naturalhandyman.com
If this information has been valuable to you, please consider making a small donation to support NH's free service to the home repair community! For more information, please visit our "Friends" page www.naturalhandyman.com/friends
The Natural Handyman Site Directory
- Home Repair Articles www.naturalhandyman.com/iip
- Home Repair Links Library www.naturalhandyman.com/linkslibrary
- NH's Bookshop www.naturalhandyman.com/bookshop
- Find a handyman at www.naturalhandyman.com/network
- Win unique home repair gifts and prizes at www.naturalhandyman.com/contest
Please read the important copyright and disclaimer information is located at www.naturalhandyman.com/copyright
More Tips & Tools to Help You
Live Better...For Less
- 6 cheap, effective home security solutions
- 5 frugal ways to expand your living space
- Top 10 DIY mistakes made by home 'handymen'
- Your trickiest cleaning problems solved
- How to eliminate mosquitos for less Insider Report
- Choosing a roadside assistance plan
- Should I use a HELOC for home remodeling and repairs
- Find the best mortgage rates in your area
- 3 ways to use a mortgage calculator
- Mortgage calculator: Calculate your payment and more
- Home equity calculator: HELOC vs. line of credit
- How much can additional payments save me on my mortgage?
- Who offers the most home insurance discounts?