Wiring a Florescent Fixture
My question is on wiring a florescent light fixture. I purchased six florescent shop lights which I intended to install in a new workshop I recently built. When I opened the shop lights I discovered that they had standard three prong plugs. Since I wanted to direct-wire these lights to come on with a wall switch I decided to cut the plug off. After cutting the plug off I discovered that there was no way to determine which wire is which except that the ground wire was green. Does it matter which of the other two wires goes to the hot wire or can they be wired either way?
No, they cannot be wired either way. By switching the ground, hot, and neutral wires you may inadvertently produce an electrocution hazard in the metal frame of the fluorescent fixture. You will have to remove the cover on the fixture that hides the ballast and determine which wire in the cord is hot. The hot wire on the ballast is black, and the neutral is white. The other colors are the wires that connect the ballast to the fluorescent tube holders and to each other.
These non-commercial fixtures are generally not UL-approved for hard wiring unless there is a manufacturer's fact sheet that says it's OK. So if there is no indication that hard wiring is approved, you will have to install new replacement three-prong plugs at the now cut ends of the power cords. These plugs are available at any hardware store. To solve the ON-OFF problem, simply install an outlet box or boxes near the fixtures, and wire the boxes so that they are controlled by a single wall switch!
COPYRIGHT 1998 G.G. ALONZY
Have a small home repair question for THE NATURAL HANDYMAN? Just click here www.naturalhandyman.com/aitikia
For more home repair information, visit NH's growing list of original home repair articles and quality links www.naturalhandyman.com
If this information has been valuable to you, please consider making a small donation to support NH's free service to the home repair community! For more information, please visit our "Friends" page www.naturalhandyman.com/friends
The Natural Handyman Site Directory
- Home Repair Articles www.naturalhandyman.com/iip
- Home Repair Links Library www.naturalhandyman.com/linkslibrary
- NH's Bookshop www.naturalhandyman.com/bookshop
- Find a handyman at www.naturalhandyman.com/network
- Win unique home repair gifts and prizes at www.naturalhandyman.com/contest
Please read the important copyright and disclaimer information is located at www.naturalhandyman.com/copyright
Also in Home
- Tricks to painting interior trim
- Affordable chimney care
- Do-it-yourself brick walkways
- The pros and cons of having a homeowners association
- 5 places to find free firewood
- Homemade detergent for HE washing machines
- 5 best budget decorating tips under $20
- How to make garden stones
- 5 ways your house can make you go broke
- 5 simple and affordable luxuries for your home
- Does staging really raise a home's price?
- 5 home renovation can raise your insurance rate -- or lead to discounts
- The right way and wrong way to pay down your mortgage
- 6 cheap, effective home security solutions
- 3 ways (and 1 reason) to refinance a HELOC
- 6 home projects that don't pay for themselves
- Should I refinance my home equity line?
- Find the best mortgage rates in your area
- 3 ways to use a mortgage calculator
- Mortgage calculator: Calculate your payment and more
- Home equity calculator: HELOC vs. line of credit
- Mortgage refinance break-even calculator
- How much money can I borrow for a mortgage?