'Short Cycling' Water Well
My home has its own water well as I live in a rural area of Missouri and I have recently had a problem. My well is short cycling, meaning that the amount of times that it cycles on and off has increased dramatically for say just flushing the toilet. I feel that it has to do with the pressure tank but do not know what to do about it. Someone told me that I needed to add more air to the tank because of a possible leak in the bladder but I am unsure or the procedure. Could you please help.
W from Macks Creek, MO.
The purpose of a well pressure tank is two fold. First, by having a tank of mostly air pressurized to the level of your fresh water system, you have a reserve of pressure that allows the water pump to only run intermittently. If your electricity goes off, you will be able to draw a few gallons of water before the system goes dry. Secondly, the air in the tank absorbs the surges of water that pumps characteristically move, smoothing out the flow from your faucets.
There are two types of tanks. Older homes used a simple tank which held the cushioning air. These tanks have a standard automotive-type air valve for adding air. In newer homes or for tank replacement, a tank with an internal bladder is used. This bladder is like a balloon filled with air, which keeps air and water separate. Over time, the air in a simple well tank will be absorbed by the water. As the amount of air in the tank decreases, the tank looses its ability to hold pressure, and the well pump on-off cycle time decreases until the pump cycle causes surging at the faucets. This continuous running is potentially damaging to the pump and can literally take years off its life. A years worth of wear and tear can occur in a matter of weeks as the pump wildly cycles on and off trying to maintain pressure in your water system.
To recharge a bladderless well tank, the tank must be completely drained of water. You may need to rent a powerful air compressor to blow the air out of the tank if your tank in below grade without a convenient drain. The procedure is simple... first turn off the well pump switch or flip the circuit breaker. Open a faucet above the level of the tank to relieve all pressure in the system. Attach the compressor hose to the air valve on the tank and blow air into it. When air begins to come through the open faucet, disconnect the compressor.
Turn on your well pump and the tank will be automatically pressurized. You may close the faucet after all air is exhausted from the system. Be aware that you may experience sudden spurts of air from faucets and toilets for a day or so as the system relieves itself of air introduced by the partial draining of the system.
If you have a bladder-type tank, the tank should be pre-pressurized to the same as the low pressure setting on your pump. Usually, the bladders do not leak, so the only reason for adding air to the tank would be if you decide to increase the water pressure in your home. Conceivably, if the pressure is the tank is too low, you could overstretch or break the bladder if you were to increase the system pressure. You would not necessarily have to replace the tank, but you would lose the benefits of a bladdered tank.
To adjust the pressure in a bladdered tank, first decide on the LOW pressure you want for your system. If you are not changing the pressure, but wish to check to be sure your tank is properly charged, look at the pressure gauge near the tank and taking note of the pressure level at which the pump turns on.
To perform the charge, the pressure in the system must be released by turning off the well pump and opening a faucet. Use a compressor or a hand pump to increase the pressure in the tank to the desired level. You don't need as powerful a compressor as you do for vacating all the water from the tank. You may even use a hand pump if you want to, though it may take an eternity to increase the pressure even a small amount.
COPYRIGHT 1998 G.G. ALONZY
Have a small home repair question for THE NATURAL HANDYMAN? Just click here www.naturalhandyman.com/aitikia
For more home repair information, visit NH's growing list of original home repair articles and quality links www.naturalhandyman.com
If this information has been valuable to you, please consider making a small donation to support NH's free service to the home repair community! For more information, please visit our "Friends" page www.naturalhandyman.com/friends
The Natural Handyman Site Directory
- Home Repair Articles www.naturalhandyman.com/iip
- Home Repair Links Library www.naturalhandyman.com/linkslibrary
- NH's Bookshop www.naturalhandyman.com/bookshop
- Find a handyman at www.naturalhandyman.com/network
- Win unique home repair gifts and prizes at www.naturalhandyman.com/contest
Please read the important copyright and disclaimer information is located at www.naturalhandyman.com/copyright
More Tips & Tools to Help You
Live Better...For Less
- 6 cheap, effective home security solutions
- 5 frugal ways to expand your living space
- Top 10 DIY mistakes made by home 'handymen'
- A comparison of cordless tools: Is cheapest the most frugal?
- How to avoid overloaded electric this Christmas
- Two routines to keep your home running smoothly
- Homemade wrinkle releaser
- Being prepared for a power outage
- Burn corn to heat your home
- Find the best mortgage rates in your area
- 3 ways to use a mortgage calculator
- Mortgage calculator: Calculate your payment and more
- Home equity calculator: HELOC vs. line of credit
- Should I borrow from my home equity?
- How much can additional payments save me on my mortgage?
- Who offers the most home insurance discounts?