Insulating a Floor
COPYRIGHT 1999 G.G. ALONZY
We have recently converted 1/2 of our garage into an extra bedroom. We live in Massachusetts where we have a cold winter climate. The garage floor is a concrete slab on grade. Needless to say our heating bill for the winter was very high. The walls and roof have been insulated with fiberglass batt insulation and we are in the process of insulating the floor. We are planning to lay 2x4's on their sides, 24 inches on center. Then we are laying 2 ft x 8 ft x 2 inch thick rigid insulation sheets between the 2x4's.
Then we are applying a 6 mil polyethylene vapor barrier over the entire area which will be covered by 3/4 inch plywood underlayment, a carpet pad and carpeting. We are also considering topping off the rigid insulation (about 1-1/2 inches) with loose fill insulation as normally used in attics. Is this a good method of reducing heat loss through the floor? Should the vapor barrier be above the insulation or below on the concrete slab? Any other suggestions?
BS from Tewksbury, MA
Sounds like a good plan! I do have a couple of suggestions. First, there is no reason to use 2x4's. 2x3's are plenty adequate (unless you can't get them long enough for your purposes). Some folks even use 1x2's, though I like the increased rigidity of the 2x3's and the extra space for insulation, You should nail them to the floor (every three or four feet is plenty) with a power nailer so everything stays put! This will insure that the floor will not do anything surprising over time. Oh... be sure that the lumber you use is straight and has been acclimated to room temperature for at least a few days or longer to minimize warping and shrinkage. Don't under any circumstances use wet wood... you'll be sorry!
Though 24" on center is acceptable from a load standpoint... obviously the 2x3's will not sag since they are on the slab... using a 16" on center installation will give you a more rigid floor surface. The vapor barrier should be right on the concrete. If you sandwich wood between the vapor barrier and the concrete, it will absorb moisture and eventually begin to rot... big time trouble!! It is better that the wood be allowed to breathe and reach a normal room moisture level.
As far as laying extra loose insulation upon the rigid insulation, my question to you is... why?? Once the oak floor is installed and the slab is essentially sealed under the floor, it is no longer cooled by the outside. The extra insulation will only give mice a great nesting place. If you feel the urge to add more insulation anyway, use additional rigid insulation instead. As an aside, you should check with your building inspector to see if you can legally run electrical wiring under the floor. If you don't have another convenient way to run the wires, this might be a helpful timesaver.
Have a small home repair question for THE NATURAL HANDYMAN? Just click here www.naturalhandyman.com/aitikia
For more home repair information, visit NH's growing list of original home repair articles and quality links www.naturalhandyman.com
If this information has been valuable to you, please consider making a small donation to support NH's free service to the home repair community! For more information, please visit our "Friends" page www.naturalhandyman.com/friends
The Natural Handyman Site Directory
- Home Repair Articles www.naturalhandyman.com/iip
- Home Repair Links Library www.naturalhandyman.com/linkslibrary
- NH's Bookshop www.naturalhandyman.com/bookshop
- Find a handyman at www.naturalhandyman.com/network
- Win unique home repair gifts and prizes at www.naturalhandyman.com/contest
Please read the important copyright and disclaimer information is located at www.naturalhandyman.com/copyright
Also in Home
- 5 ways your house can make you go broke
- 5 simple and affordable luxuries for your home
- 12 ways to lower heating bills
- Will my insurance spike if I rent out my basement?
- Why pay extra toward mortgage principal?
- 5 tips to sell a home before buying another
- 6 ways to stock your "man cave" for under $500
- 6 home projects that don't pay for themselves
- Should I refinance my home equity line?